Iplex Pipelines Australia Pty Ltd—K1 25mm x 20mm BSP Male Adaptor (Part no: FK1522520)
What are the defects?
In some instances the fitting has cracked when crimped to 25mm K1 multilayer gas pipe.
What are the hazards?
If the crack is undetected at the time of installation or during subsequent pressure testing, gas leakage may occur.
What should consumers do?
Consumers and gas fitters who have purchased the fitting from the nominated outlets between 6 March and 3 August 2012 should immediately contact Iplex Pipelines to arrange a replacement of the fitting at no cost to the consumer.
Contact Iplex Pipelines, Grant Murray or Kym Overs telephone 13 18 40 or email firstname.lastname@example.org
Tradelink Plumbing Supplies and Swan Plumbing Supplies
- 6 March 2012 - 3 August 2012
Recall advertisements and supporting documentation
Australian Competition and Consumer Commission is the responsible regulator for this recall.