Clipsal Australia Pty Ltd—IP56 rated—Industrial HD Load Break Switch
What are the defects?
The problem is an eventual fracture of a non-compliant plastic part which can lead to the non load-breaking of one or more phases. The pole may remain electrically connected even if the switch is in the O position (OFF).
What are the hazards?
What should consumers do?
Customers are advised to ensure that all electrical circuits, where there Load Break Switch is installed, are fully disconnected (using voltage detectors) before conducting any electrical installation or maintenance work. Further information is available from the Customer Satisfaction and Quality Manager on telephone number 08 8269 0565.
Australian Competition and Consumer Commission is the responsible regulator for this recall.